EWAD620C6SL | EWAD730C6SL | EWAD830C6SL | EWAD910C6SL | EWAD960C6SL | EWADC10C6SL | EWADC11C6SL | EWADC12C6SL | EWADC13C6SL | EWADC14C6SL | EWADC15C6SL | EWADC16C6SL | EWADC17C6SL | |||||
---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|

Cooling capacity | Nom. | kW | 618 (1) | 726 (1) | 826 (1) | 907 (1) | 960 (1) | 1,058 (1) | 1,148 (1) | 1,342 (1) | 1,466 (1) | 1,705 (1) | 1,812 (1) | 1,908 (1) | 1,975 (1) | ||

Capacity control | Method | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | |||

Minimum capacity | % | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 7.0 | 7.0 | 7.0 | 7.0 | |||

Power input | Cooling | Nom. | kW | 210 (1) | 262 (1) | 307 (1) | 325 (1) | 361 (1) | 385 (1) | 406 (1) | 463 (1) | 516 (1) | 627 (1) | 694 (1) | 728 (1) | 782 (1) | |

EER | 2.94 (1) | 2.77 (1) | 2.69 (1) | 2.79 (1) | 2.66 (1) | 2.75 (1) | 2.83 (1) | 2.90 (1) | 2.84 (1) | 2.72 (1) | 2.61 (1) | 2.62 (1) | 2.52 (1) | ||||

ESEER | 4.02 | 3.90 | 3.93 | 3.91 | 3.77 | 3.88 | 3.90 | 4.02 | 3.98 | 3.78 | 3.83 | 3.59 | 3.71 | ||||

Dimensions | Unit | Depth | mm | 6,285 | 6,285 | 6,285 | 6,285 | 6,285 | 7,185 | 8,085 | 8,985 | 8,985 | 11,185 | 11,185 | 12,085 | 12,085 | |

Height | mm | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | 2,540 | |||

Width | mm | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | 2,285 | |||

Weight | Operation weight | kg | 6,200 | 6,280 | 6,300 | 6,820 | 7,100 | 7,540 | 7,810 | 8,570 | 8,570 | 11,700 | 12,560 | 12,920 | 12,920 | ||

Unit | kg | 5,920 | 6,030 | 6,050 | 6,570 | 6,850 | 7,300 | 7,570 | 8,190 | 8,190 | 11,210 | 11,680 | 12,040 | 12,040 | |||

Water heat exchanger | Type | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | |||

Water volume | l | 266 | 266 | 251 | 251 | 251 | 243 | 243 | 386 | 386 | 474 | 850 | 850 | 850 | |||

Air heat exchanger | Type | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | |||

Fan | Air flow rate | Cooling | Nom. | l/s | 49,943 | 49,943 | 49,943 | 59,932 | 59,932 | 69,921 | 79,909 | 89,898 | 89,898 | 109,875 | 109,875 | 119,864 | 119,864 |

Fan motor | Speed | Cooling | Nom. | rpm | 850 | 850 | 850 | 850 | 850 | 850 | 850 | 850 | 850 | 850 | 850 | 850 | 850 |

Compressor | Quantity | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 3 | 3 | 3 | 3 | |||

Type | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | ||||

Sound power level | Cooling | Nom. | dBA | 98 | 98 | 98 | 100 | 99 | 100 | 100 | 100 | 100 | 102 | 102 | 103 | 103 | |

Sound pressure level | Cooling | Nom. | dBA | 78 (2) | 78 (2) | 78 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 80 (2) | 80 (2) | 80 (2) | |

Refrigerant | Type | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | |||

Circuits | Quantity | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 3 | 3 | 3 | 3 | |||

Power supply | Phase | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | |||

Frequency | Hz | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | |||

Voltage | V | 380 | 380 | 380 | 380 | 380 | 380 | 380 | 380 | 380 | 380 | 380 | 380 | 380 | |||

Compressor | Starting method | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | |||

Notes | (1) - Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | (1) - Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | (1) - Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | ||||||||||||||

(2) - Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | (2) - Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | (2) - Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | |||||||||||||||

(3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (3) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | |||||

(4) - Maximum starting current: starting current of biggest compressor + 75 % of maximum current of the other compressor + fans current for the circuit at 75 % | (4) - Maximum starting current: starting current of biggest compressor + 75 % of maximum current of the other compressor + fans current for the circuit at 75 % | (4) - Maximum starting current: starting current of biggest compressor + 75 % of maximum current of the other compressor + fans current for the circuit at 75 % | |||||||||||||||

(5) - Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | (5) - Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | (5) - Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | |||||||||||||||

(6) - Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | (6) - Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | (6) - Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | |||||||||||||||

(7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (7) - Maximum unit current for wires sizing is based on minimum allowed voltage. | |||||

(8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (8) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | |||||

(9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water | (9) - Fluid: Water |